Multi-fold input/output element with isolator
MHY 925 is an addressable multi-fold element containing 8 (4) programmable inputs and 8 (4) programmable outputs.
MHY 925 is an addressable multi-fold element containing 8 (4) programmable inputs and 8 (4) programmable outputs. It connects to a detection loop of analogue addressablecontrol panels LITES, and when supplemented with appropriate module also to SL-RS 485 communication line of control panels MHU 115 and MHU 116/117. The element containsan isolator.
Inputs serve for automatic signalling of pre-defined exceptional states of any external device, which signals this state by either closing or opening an electronic contact, or by voltage applied to opto-isolated input. Inputs can also be set as monitored.
Outputs serve for controlling of external devices connected to device’s switch-over NO/NC contacts.
MHY 925 comes in two types:
- a) MHY 925/4 – contains 4 programmable inputs and 4 programmable outputs
- b) MHY 925/8 – contains 8 programmable inputs and 8 programmable outputs
Input/output element MHY 925 can be connected to a detection loops of control panels MHU 110, MHU 111, MHU 115, MHU 116 and MHU 117. After adding the DLS 925 communication module the MHY 925 can be connected to SL-RS 485 communication line of control panels MHU 115, MHU 116 and MHU 117.
Properties of each input and conditions of outputs activation are defined in configuration program for control panels.
Electronic circuits of element MHY 925 are on a PCB that is placed in a plastic box with removable cover. Communication module DLS 925 connects to a connector and is secured with spacers on the PCB.
The element is powered by impulse voltage from detection line of control panel, or if connected to communication line SL-RS 485, from control panel’s source or from external backup power supply. Input lines can be connected as opto-isolated, or as closing/opening contact. These inputs can also be set as monitored, where the opening contact (fault) and closing contact (fire alarm) of the connected external device can be connected simultaneously. At the same time the input lines are monitored for interruption and short-circuit.
Outputs are bistable relays with switch-over potential-free contacts.
The addressable part registers the control panel’s communication, reports own address and sends information when input is activated or activates own output.